I have several 2nd floor floor joists that sag to as much as 1 5/8 inches. They do not look broken or rotted. How much would it cost to replace them and are they safe the way they are?
The Joists are about 16 feet across and the entire floor will be replaced anyway.
1 5/8" deflection is quite substantial!
The first concern is to see if any renovation has been done on the second floor that may have redirected the load path above or created a point load somewhere in the midspan of the joists. This should be verified before any repair begins. Another common problem is that the joists have been compromised by cutting or notching for utilities, particularly plumbing in bathrooms. Look closely for this.
If that is not the case, you can open the ceiling below and temporarily remove the electrical, plumbing and HVAC. At this point you can temporarily and slowly jack up the sagging joists. Once they are as close to straight and level as possible you can "sister" a new joist beside each existing joist using construction adhesive and nails or screws. The number and pattern of fasteners will be prescribed in the Ontario Building Code 2006.
It is important to note that unless these "sistered" joists bear on both bearing points (typically the outside wall and an interior load bearing wall) they are NOT increasing the strength of the floor but are simply re-establishing a level floor and greatly stiffening the existing framing. If you can get full length joists from bearing point to bearing point you will be increasing the strength of the floor above.
This will be all dependent on the load above, and while sagging is common in older structures it can never be simply dismissed as "an old structure". Something is causing the sagging and that should definitely be identified and addressed first.
This is one of the more involved and potentially dangerous (possibly catastrophically) jobs to tackle in a home as it often involves all of the mechanical trades as well as major structural aspects of the building.
If you are not well versed in building sciences I would urge you to retain the services of a professional contractor in your area or a Structural Engineer (P.Eng) yourself if you plan on attempting the repair.
That 1 5/8" deflection is cause for concern.
I hope this helps.
The Cedarbrook Group
It depends on what flooring you have down that will have to come up to do so and what flooring you choose to put back down, the actual joint replacement is not that expensive.
Mike McInnis o/o of McInnis Contracting.
Need help designing or revovation your home? Post your project and get free estimates from top-rated pros.Click here to get started - It's Free! Trustedpros Inc. does not warrant the accuracy, completeness, safety, legality or usefulness of any Content, or Whether Content is Current and up-to-date, and TrustedPros Inc. Shall have no liability whatsoever with respect to your use or reliance upon any content or for content being removed or otherwise ceasing to be available. Please refer to the terms and conditions of use of this websites for more details.
Use TrustedPros to post your project and receive bids from to-rated local contractors. Posting your project is fast, free and easy to use. It gives you the tools to manage your projects, negotiate the best rates and find the right contractor for your project.Post Your Project
Use the TrustedPros directory to browse profiles, read real customer reviews and find the best local contractor.Search for Pros
Browse thousand of beautiful home design and renovation photos.Browse Photos
Help other homeowners find the right contractor or avoid the bad ones by submitting your reviews today.Write a Review